Renewable energyTALOS® ECUTHERM™ SOLAR
Solar system networks
TALOS® copper tubes are manufactured according to European and U.S. Specifications and have been certified by most international quality organizations (RAL/DVGW, BSI, AFNOR, AENOR, CSTB, NSAI, KIWA / GASTEC-QA, GOST, VIK, SITAC, STF VTT).
High Performance Technological Product
TALOS® ECUTHERM™ SOLAR copper tubes are coated with a 3-layer system. To begin with, a high-temperature resistant PES insulation layer is positioned on the outside of the copper tube. furthermore, an industrial insulation of cross-linked polyethylene (PE-X) foam structured in closed micro-cells provides thermal insulation. On top of that , an external covering creates an integral resistance barrier against the external environment.
Copper Tube Technical Characteristics
Phosphorus deoxidized copper (DHP-CU) in soft temper (R220), according to EN 1057..
Insulation Technical Properties
PE-X or PE foam
DENSITY ACCORDING TO DIN 53420 ASTM D 1667
THERMAL CONDUCTIVITY COEFFICIENT (λ) ACCORDING TO EN ISO 8497
0.0357 W/mK (0oC)
0,0389 W/mK (40oC)
VAPOUR-WATER DIFFUSSION RESISTANCE COEFFICIENT (μ) ACCORDING TO EN 13469
-80oC to +110oC(+90oC for PE foam)
EN 13501–1, Class B or Class E, DIN 4102, B2, BS 476, NF P 92 501-M1
RESISTANCE TO CHEMICAL AGENTS ACC. TO ASTM 543-56 T
DIMENSIONAL STABILITY ACCORDING TO ISO 2796 FOR TEMPERATURES UP TO 1000C
Values are listed, as obtained under standard laboratory conditions and may be amended, without prior notice.
(Roll Lengths 10, 15, 20, 25 meters) Talos ECUTHERM™ Solar
|Outside diameter of copper tube mm||Wall thickness mm||Total diameter with 13mm thick insulation||Bend Radius|
Standardized Dimensions Talos ECUTHERM™ Solar 2
12/12, 15/15, 18/18, 22/22
Cable Technical Characteristics
|CONDUCTOR MATERIAL||Flexibility of conductor||Color||No. of poles||Nominal voltage Vo/V||Nominal cross section of conductor|
|COPPER||Flexible, CLASS E||White||2||300/300||2 X 0,75 mm2|